A fresh produce manufacturing company has been fined £170,000 after a worker was killed after coming into contact with a live 240V electrical cable.
Chichester Crown Court was told that, Bradley Watts, a 21 year old sub-contractor, was lagging pipes in the loft space of Natures Ways Foods premises in Chichester, on 2 June 2011. He came into contact with a 240V live electrical cable and was electrocuted. He was pronounced dead at the scene by the ambulance crew.
The live cable was part of an old system that had been removed by Natures Way Foods in 2008, but was not identified in any way, and its existence and ‘live’ nature was unknown to Natures Way Foods. An investigation by HSE concluded that
Natures Way Foods had plenty of opportunity to deal with redundant cables but it was always assumed they were not live. Had the old cabling been removed in a systematic and controlled manner, or subsequent checks of the loft space identified the examples of poor practice, the death of Bradley Watts could have been avoided.
The company, of Selsey, West Sussex, pleaded guilty to breaching sections 2(1) and 3(1) of the Health and Safety at Work etc Act 1974. It was fined £170,000 and must pay costs of £35,403.
More information about Electrical safety can be found at http://www.hse.gov.uk/safemaintenance/heavy-items.htm
Notes to Editors:
- The Health and Safety Executive is Britain’s national regulator for workplace health and safety. It aims to reduce work-related death, injury and ill health. It does so through research, information and advice, promoting training, new or revised regulations and codes of practice, and working with local authority partners by inspection, investigation and enforcement. hse.gov.uk
- Section 2(1) of the Health and Safety at Work Etc. Act 1974 states: “It shall be the duty of every employer to ensure, so far as is reasonably practicable, the health, safety and welfare at work of all his employees.
- Further HSE news releases are available at press.hse.gov.uk